BPSMS 10-300KVA Modular type UPS:
Nominal voltage: 380/400/415VAC
Output power factor: 1
BPSMS series Modular type UPS is modular online UPS for sensitive equipments. The single cabinet power rating covers from 10KVA to 300KVA which delivers the best of combination of reliability, hot-swappable and flexibility. With the latest IGBT three-level technology and DPS control, BPSM achieves a high input power factor, low THDi Modular design with N+X redundancy and online hot swapping, easy to expand the capacity Full DSP control of high stability, reliability and safety Integrated IGBT module with improved performance and reduced size.
BPSMS 10-300KVA Modular type UPS Applicaitons:
IDC (Internet Data Center) , computing center, ISP (Internet Service Provider ),Telecom,Finance bank and securities,Tax, hospital system, industrial automation, precision equipment, etc.
BPSMS 10-300KVA Modular type UPS Key Features:
- Superior energy saving and environment-friendly:
Efficiency > 96% at 50%-75% rated load, and > 95% at 25% rated load; Input PF > 0.99,input THDi<3%
Top or bottom cabling, no need of input cabling cabinet.
Full front access, UPS, failed part can be replaced shortly
The number of battery cells can be configured flexibly, so the original batteries can be used when modifying the legacy system; moreover,
the battery cell can be replaced in time when it fails without interrupting the normal operation of modular type UPS.
- Extra large LCD that can display 13 language(Chinese, English ,Russian, French ,Spanish and so on )
- Provide large LCD touch screen (optional)
- Each UPS module provide 4.5KW charge capacity, equivalent to 10-12A
- Advanced DSP full digital control technologies realize higher system stability, online capacity expansion and maintenance.
- Advanced distributed active parallel technology realizes parallel operation of 4 UPS units and online capacity expansion without
centralized bypass cabinet.
- Adaptive to servere power grid environment due to extra wide input voltage and frequency ranges.
- intelligent battery management maintains battery automatically to prolong the battery life.
- the machine system for modular structure, consist of 1 to 10 module’s biggest single module is 30 kw.
- UPS power module supporting hot swappable, capacity upgrade extremely simple.
- Super ability for overload and short circuit, ensure the system stability and safety under the limit state of system.
BPSMS 10-300KVA Modular type UPS technical specifications:
|Input voltage||380V/400V/415AC(Optional South America 208v)|
|Input Frequency Range||50/60Hz|
|Power Factor||Full load>0.99 ,Half load >0. 98|
|Input power soft-start fantion||5-30s settable|
|Input Voltage Ranges||228V-476V-20%- +25% Full load linear derating at -25% – -40%; can take 70% load at -40%|
|Battery Voltage||±240VDC(Default),12V Battery30-40pcs can be choose|
|Charge Voltage accuracy||± 1%|
|Bypass Input voltage||380/400/415VAC 3-phase 4-wire|
|Voltage Ranges||Default value is -20%-+15%, -40%, -30%, -10% – +10%, other ranges can be set viasoftware|
|Overload Capacity||150%,long term operation,150%<load1000% 100ms</load|
|Inverter Output Voltage||380/400/415VAC 3-phase 4-wire|
|Voltage Accuracy||± 0.5%(balanced load), ± 1% (unbalanced load)|
|THDV||THDV<1%(linear load), THDV<3%(nonlinear load)|
|Three Phase Angle accuracy||120°c ± 0.5°c|
|Current Crest Ratio||03:01|
|Transfer Time||0ms,15ms(ECO Mode)|
|Mains synchronization range||±2Hz(Default value) adjustable with step of 0.5Hz within range of +/- 0.5Hz – 3Hz|
|Communication Ports||RS232,RS485,dry contact,SNMP card,EPO,generator port|
|System efficiency||> 96% at load above 50%, >95% at load above 25%|
|Operation Temperature||0-40 °c|
|Storage Temperature||-25 °c -70 °c (without battery)|
|Noise(dB)||55-62dB,Adjusted with load|
|Weight||5 module cabinet||module :RMS050/10, RMS100/20, RMS150/30||150KG|
|10 module cabinet||module :RMS100/10, RMS200/20, RMS300/30||180KG|
|module :PM10||10KVA power module :28KG|
|module :PM20||20KVA power module :30KG|
|module :PM30||30KVA power module :35KG|
|Dimendion(W XD XH)mm||5 module cabinet||600X1400X850|
|10 module cabinet||600X2070X850|
Working principle of BPSMS 10-300KVA Modular type UPS
Modular UPS use double conversion online structure, including the rectifier, inverter, battery charger, control circuit, the input and output battery connector breaker, have function that is input power factor compensation. All modules can be online hot-swappable, provide the highest level of availability, and maintainability.
If one power module failure will not affect the system normal working, power module can be online hot-swappable all power module parallel is managed by the control board, in accordance with the unified parameters running, one power module fault can be automatically exit parallel system, will not cause harm to the whole parallel system.
Modular UPS system use independent static bypass module, do not use multiple static bypass structure, avoid causing overload to damage the modules, because of multiple bypass module uneven current when UPS turn to bypass working.
Module parallel output voltage accuracy is ±1%, parallel circulation current < 1%. Static bypass module contains bypass static swith only, excluded static switch of the main circuit output, therefore, replacing static bypass module will not cause the system power down or transfer manual maintenance bypass, which can realize online hot-swap replacement.
Modular type UPS host introduction
The power module of Modular type UPS uses double conversion on-line structure, including the rectifier, inverter, charger, control circuit, and the input output battery bus of the circuit breaker. With input power factor compensation. All modules can be replaced online hot swap, to provide the highest level of availability, maintainability.
The modular type UPS host control module adopts industrial BUS CAN bus control structure, which is controlled by two redundant modules to complete the control and management of the system. A control module failure will not affect the normal operation of the system. Control module can be online hot swap replacement. Power modules are connected in parallel by the control module centralized management, in accordance with the unified and machine parameters to run, a power module fault can automatically exit the parallel system, not on the entire parallel system.
The modular type UPS system adopts an independent static bypass module, which does not use a number of static bypass structures, so as to avoid the overload damage caused by multiple bypass of bypass. The accuracy of the output voltage of the module is + 1%, and the circulating current is <1%.
Standard SNMP card, using HTTP protocol, SNMP protocol, TELNET protocol, etc.. The modular type UPS in the city state of electricity, battery state, the state of the bypass, inverter, the self state, boot state and input voltage, output voltage, percentage of load, the input frequency, the voltage of the battery, battery capacity, battery discharge time, UPS machine temperature, surrounding temperature and so on UPS run at a glance, to improve the efficiency and quality of the modular type UPS power supply security system management. Selection of open windows2000/windowsXP/windows2003 windowsNT/ operating system platform.
The temperature and humidity sensor can be selected, and the multifunctional network card is inserted, and the temperature and humidity monitoring and alarming of the computer room environment can be realized through the network.